- Product Catalog
- Power cables with plastic insulation with a rated voltage of up to 3 and 6 kilovolts
- VVG-PNG (A) -LS, AVVG-PNG (A) –LS
VVG-PNG (A) -LS, AVVG-PNG (A) –LS
Applying area and purpose
Cables are designed for transmission and distribution of electric energy in stationary electrical installations at a rated alternating voltage of 0.66 and 1 kV with a frequency of 50 Hz
Cables are used for electrical wiring in residential and public buildings.
Cables are intended for operation in cable structures and premises, including for nuclear facilities in nuclear power systems of classes 3 and 4 according to the classification OPB-88 (PNAEG - 01-011-97).
Fire hazard class of cables according to NATIONAL QUALITY STANDARD 31565 P1b.18.104.22.168.
|Rated voltage, kV||0,66 or 3|
|Ambient temperature during cable use||from -50 to +50|
|Minimum bending radius cable diameters||10|
|Cables are laid at a temperature (without preheating), ° С, not lower||-15|
|Smoke in the test chamber||Not more than 50%|
Copper or aluminum, single-wire, round, 1 class according to NATIONAL QUALITY STANDARD 22483.
Number of cores 2 and 3
Nominal cross section, mm2
Copper 1.5 - 16
Aluminum 2.5 - 16
PVC compound of reduced fire hazard (color cores).
Location of veins
Insulated cores are laid parallel in one plane.
PVC compound of reduced fire hazard.