- Product Catalog
- Power cables with plastic insulation with a rated voltage of up to 3 and 6 kilovolts
- PVVGNG (A) -FRLS, PVVGENG (A) -FRLS, PVBSHVNG (A) -FRLS
PVVGNG (A) -FRLS, PVVGENG (A) -FRLS, PVBSHVNG (A) -FRLS
Applying area and purpose
Cables are designed for transmission and distribution of electric energy in stationary electrical installations at a rated alternating voltage of 0.66 and 1 kV with a frequency of 50 Hz
Cables are used for group cabling of power supply lines for electrical equipment of security systems, electrical wiring of fire safety systems (power supply for fire extinguishing pumps, lighting of emergency exits and escape routes, smoke extraction and ventilation systems, evacuation elevators), for wiring in operating rooms of hospitals, emergency power supply and equipment supply circuits (current collectors) functioning in case of fire. It remains operational in case of fire for 180 or 240 minutes.
Fire hazard class of cables according to NATIONAL QUALITY STANDARD 31565 P1b.22.214.171.124.2
|Rated voltage, kV||0,66 or 1|
|Ambient temperature during cable use °С||from -50 to +50|
Minimum bending radius cable diameters
|For single core and flat||10|
|Cables are laid at a temperature (without preheating), ° С, not lower||-15|
|Smoke in the test chamber||Not more than 50%|
Copper, single-wire or multi-wire, round or sector shape, class 1 or 2 according to NATIONAL QUALITY STANDARD 22483, cross-section from 1.5 to 1000 mm2.
Thermal barrier according to thermal conductivity
Winding of two glass-mica tapes with overlapping.
Insulated conductors of 2, 3, 4 and 5 core cables are twisted into a core.
PVC compound low fire hazard.
It is imposed by a winding of one mica tape or one glass tape.
Additional thermal barrier (for "FE 240")
It is imposed by a winding of one or two mica-containing tapes.
For cables of the brand PvVGEng (A) -FRLS it is made in the form of a winding from copper tapes or from copper wires and a spirally applied copper tape.
For cables of the PvVGEng (A) -FRLS brand from glass tape or mica tape with a winding with overlapping.
For cables of the PvBShvng (A) -FRLS brand, it is laid spirally from two steel galvanized tapes over a thermal barrier.
Outer sheath or protective hose PVC compound low fire hazard