Applying area and purpose
Cables are designed for electrical installations for stationary installation in lighting and power networks, as well as for the installation of electrical equipment, machinery, mechanisms and machines for rated alternating voltage up to 220/380 V, frequency up to 400 Hz or direct voltage up to 700 V inclusive.
Cables do not spread combustion during group stationary laying of cable lines, provided that there are no mechanical influences on the cable and remain operational when exposed to a flame for at least 180 minutes.
Designed for electrical wiring and emergency power supply circuits and equipment (current collectors) in residential and public buildings, in operating rooms of hospitals, in office rooms equipped with computer technology and microprocessor technology, spectacular complexes and sports facilities, as well as other facilities with increased fire safety requirements in the presence of risk of mechanical damage during operation, if the cable is not subjected to significant tensile forces, as well as to protect against rodents.
Fire hazard class of cables according to national quality standard 31565 P1b.220.127.116.11.
Number of cores from 2 to 5.
Copper single-wire class 1 (for cross sections from 0.5 to 10 mm2), or multi-wire round class 2 (for cross-section 16 mm2), or for cables with flexible conductors - class 5 (for cross-sections from 0.5 to 16 mm2).
Ceramic forming silicone rubber.
Insulated conductors of 2 - 5 core cables are twisted.
PVC compound low fire hazard.
Galvanized steel braid.
PVC compound of reduced fire hazard.