KPSSng (A) -FRLS, KPSSng (A) -FRLS, KPSSng (A) -FRLS, KPSSGng (A) –FRLS
Applying area and purpose
Designed for single or group stationary laying in fire protection systems, fire alarm systems, warning and evacuation of people in case of fire, in buildings, structures and structures (industrial enterprises, schools, hospitals, office buildings, high-rise buildings, metro, nuclear power plants) , where requirements are made for cables and wires to maintain operability in a fire. They remain operational during a fire for 240 minutes. It is operated indoors and outdoors, subject to protection from direct exposure to solar radiation and atmospheric precipitation.
Fire hazard class according to national quality standard 31565 P1b.18.104.22.168.
Copper, single-wire, 1 class or multi-wire not lower than 3 classes according to national quality standard 22483, cross section from 0.2; 0.35; 0.5; 0.75; 1.0; 1.5; 2.5 mm2.
Silicone rubber (color coding).
Isolated cores are twisted in pairs.
It is imposed by winding of one micra tape over each twisted pair.
In cables with two pairs, twisted pairs wrapped with mica tape are arranged in parallel.
For cables of grades KPSESng (A) -FRLS, KPSESGng (A) -FRLS over the thermal barrier is applied by winding or longitudinally overlapping with contact conductor of tinned copper wire.
PVC compound low fire hazard.