- Product Catalog
- Power cables with plastic insulation with a rated voltage of up to 3 and 6 kilovolts
- PVVG, APVVG, PVVGE, APVVGE, PVBSHV, APVBSHV, PVVG-P, APVVG-P, PVBSHP, APVBSHP
PVVG, APVVG, PVVGE, APVVGE, PVBSHV, APVBSHV, PVVG-P, APVVG-P, PVBSHP, APVBSHP
Applying area and purpose
Cables are designed for transmission and distribution of electric energy in stationary electrical installations at a rated alternating voltage of 0.66; 1 and 3 kV with a frequency of 50 Hz.
Cable ducts for laying single cable lines.
Cables of the PvBShv, APvBShv model, in single-core execution.
Fire hazard class of cables according to NATIONAL QUALITY STANDARD 31565 O22.214.171.124.4.
|Rated voltage, kV||0,66; 1 or 3|
|Ambient temperature during cable operation ° С||from -50 of +50|
|Minimum bending radius||For stranded||7,5|
|For single and flat||10|
|Cables are laid at a temperature (without preheating), ° С, not less||-15|
Copper or aluminum, single-wire or multi-wire, round or sector shape, class 1 or 2 according to NATIONAL QUALITY STANDARD 22483. Nominal cross-section of the main conductors, mm2 from 1.5 to 400.
Crosslinked polyethylene (color cores).
Insulated conductors of 2, 3, 4 and 5 core cables are twisted into a core. For cables of brands PvVG-P, APvVG-P, insulated conductors are located in parallel in one plane.
Made by extruding from PVC compound with filling the external spaces between the insulated conductors or (for unarmoured cables with copper sector conductors) winding from PVC tapes with filling the external spaces between the insulated conductors corbels (bundles). For cables of brands PvBShp, APvBShp made by extrusion of PVC compound or cross-linked polyethylene.
For PvVGE, APvVGE is made in the form of a winding from copper tapes or, in agreement with the customer, from copper wires and spirally applied copper tape.
For PvBShv, APvBShv, PvBShp, APvBShp it is imposed spirally from two steel galvanized tapes.
Outer sheath or protective hose For PvVG, PvVG-P, PvVGE, APvVG, APvVG-P, APvVGE, PvBShv, APvBShv - PVC compound.
For PvBShp, APvBShp from polyethylene.