- Product Catalog
- Power cables with plastic insulation with a rated voltage of up to 3 and 6 kilovolts
- PVBSHVNG (V), APVBSHVNG (V)
PVBSHVNG (V), APVBSHVNG (V)
Applying area and purpose
Cables of models PVBSHVNG (V), APVBSHVNG (V) are intended for group laying in cable structures and premises.
Cables of models PVBSHVNG (V), APVBSHVNG (V) in single core design are designed for operation in direct voltage networks.
Fire hazard class of cables according to NATIONAL QUALITY STANDARD 31565 P184.108.40.206.4.
|Rated voltage, kV||0,66; 1 or 3|
|Ambient temperature during cable use||from -50 or +50|
|Minimum bending radius
|For single core and flat||10|
|Cables are laid at a temperature (without preheating), ° С, not lower||-15|
Copper or aluminum, single-wire or multi-wire, round or sector shape, 1 or 2 classes according to NATIONAL QUALITY STANDARD 22483.
Nominal section of the main veins, mm2 From 1.5 to 4 00.
Crosslinked polyethylene (color cores).
Insulated conductors of 2, 3, 4 and 5 core cables are twisted into a core.
Made by extrusion of low flammability PVC compound with filling of the outer gaps between the insulated cores.
Superimposed spirally from two galvanized steel tapes.
Outer sheath or protective hose Made of low flammability PVC compound.