KVVG, KVVGZ, KVVGE, KVBBSHV
Applying area and purpose
Cables are designed for fixed connection to electric devices, apparatuses, terminal assemblies of electrical switchgears with rated alternating voltage up to 660 in frequencies up to 100 Hz or constant voltage up to 1000 V.
Kvvg cable is used for laying in rooms, channels, tunnels, in aggressive environments, in the absence of mechanical stress on the cable.
Kvvge cable is used for laying in rooms, channels, tunnels in the absence of mechanical influences on the cable, in an aggressive environment and the need to protect electrical circuits from the influence of external electric fields.
A cable of the kvbshv brand is used for laying in rooms, channels, tunnels in aggressive environments and in places exposed to stray currents, if the cable was not subjected to significant tensile forces.
The KVVGZ cable is used for electrical installations that require cable glands during entry.
Fire hazard class according to NATIONAL QUALITY STANDARD 31565 o220.127.116.11.4.
|Rated voltage, kV||
|Ambient temperature during cable operation, ° С||
from - 50
to + 50
Minimum bending radius, cable diameters
|armored cables during installation without preheating at an ambient temperature of at least -7 °||not less than 10|
|unarmored, at -15 ° С||
not less than 6
outer diameter up to 10 mm inclusive
|not less than 3|
outer diameter up to 10 mm to 25 mm
|not less than 4|
|Long-term permissible core heating temperature during operation, ° C||
Copper single-wire, class 1
According to NATIONAL QUALITY STANDARD 22483, section from 0.75 to 6 mm2.
From 4 to 61 isolated cores. The insulated cable conductors are twisted, in each coil there is a counting pair.
Pvc plastic compound or a layer of tapes of a polyethylene terephthalate film.
screen for cables brand kvvge. Foil aluminoflex with tinned copper contact conductor.
For cables of the kvbbshv brand, it is imposed spirally from two steel galvanized tapes.
Outer sheath or protective PVC plastic hose.