KPSVVng (A) -LS, KPSVVGng (A) -LS, KPSVEVng (A) -LS, KPSVEVGng (A) -LS, KPSVEVEVng (A) -LS, KPSVEVEVGng (A) –LS
Applying area and purpose
Cables are intended for installation of fire and security alarm systems, access control systems, as well as other control, monitoring and communication systems in the conditions of stationary laying inside buildings, structures, if necessary, to protect electrical circuits from the influence of external electric fields.
Cables do not spread combustion during group installation. Cable fire hazard class according to national quality standard 31565 P1b.22.214.171.124
Copper, single-wire 1 class or multi-wire no lower than 3 classes according to national quality standard 22483, cross section from 0.2 to 2.5 mm2
PVC compound low fire hazard (color cores).
Insulated cores are twisted in pair.
In cables with two pairs, twisted pairs are arranged in parallel.
Contact conductor of tinned copper wire is superimposed by winding or longitudinally overlapping:
Top of twisted pairs of cables KPSVEVng (A) -LS, KPSVEVGng (A) -LS;
Top of each pair individually in two-pair cables KPSVEEVng (A) -LS, KPSVEVEVGng (A) –LS
PVC compound low fire hazard.